- Do outdoor outlets need to be on their own circuit?
- What kind of GFCI outlet do I need?
- What makes a GFCI weather resistant?
- Is there a difference between an indoor and outdoor GFCI outlet?
- How do I know if my outlets are tamper resistant?
- How many receptacles can be on a 20 amp circuit?
- Do you need to baby proof tamper resistant outlets?
- Should outdoor outlets be weather resistant?
- Are weather resistant GFCI required?
- Are tamper-resistant outlets required by code?
Do outdoor outlets need to be on their own circuit?
That being said, no, outdoor outlets are not required to be on a separate circuit.
They do need to be protected by a GFCI which can either be a GFCI breaker or the familiar “outlet with buttons” wall box mounted unit..
What kind of GFCI outlet do I need?
GFCI protection is required for 125-volt to 250-volt receptacles supplied by single-phase branch circuits rated 150 volts or less to the ground. GFCI receptacles are required in bathrooms, garages, crawl spaces, basements, laundry rooms and areas where a water source is present.
What makes a GFCI weather resistant?
Weather-resistant GFCI outlets include brass and nickel plated contacts and other metal parts that resist corrosion caused by moisture. Corrosion can cause a failure of the receptacle.
Is there a difference between an indoor and outdoor GFCI outlet?
Outdoor electrical outlets differ from indoor outlets because they have watertight covers that protect the outlet even with a cord plugged in. Plus, the National Electrical Code requires all outdoor outlets to be GFCI outlets (ground fault circuit interrupter outlets).
How do I know if my outlets are tamper resistant?
How I can tell if a receptacle outlet is tamper resistant?The letters “TR” are embossed between the two vertical slots (hot and neutral).Tamper resistant receptacles use a plastic shutter just inside the two vertical slots, and it will not release unless equal pressure is applied to both of them at the same time by the two prongs of an electrical cord.Jul 22, 2018
How many receptacles can be on a 20 amp circuit?
10 receptaclesOne rule of thumb is to assign a maximum draw of 1.5 amps to each receptacle, which allows for 10 receptacles on a 20-amp circuit.
Do you need to baby proof tamper resistant outlets?
Tamper-resistant outlets reduce the risk of electrical injuries, but they are not completely tamper-proof. Unfortunately, some people believe that tamper-resistant outlets are “child proof” when they are not. Tamper-resistant outlets do not prevent children from imitating adults and inserting plugs into outlets.
Should outdoor outlets be weather resistant?
It has to be GFCI protected, and a weather-resistant type receptacle must be used. Also, the cover must be weatherproof when nothing is plugged in, though I recommend an “in-use” or “extra-duty” cover. … Article 210.8(A)(3) of the National Electrical Code, says that outdoor receptacles must be GFCI protected.
Are weather resistant GFCI required?
Required Outdoor Receptacle Locations All 15-amp and 20-amp, 120-volt receptacles must be GFCI-protected. … All 15-amp and 20-amp 120-volt nonlocking receptacles in wet or damp locations must be listed as weather-resistant type.
Are tamper-resistant outlets required by code?
All nonlocking type 15A and 20A, 125V receptacles in the following areas of a dwelling unit [210.52] must be listed as tamper-resistant [406.12]. Exception: Receptacles in the following locations aren’t required to be tamper-resistant: Receptacles located more than 5½ ft above the floor.